XBW(F)Prefabricated Substation Special for Wind-power Generation
The substation is to manufacture and assemble the support equipments for wind-power step-up stations in advance, i.e. install step-up transformer, HV switch, LV switch, supply transformer and other auxiliary devices in an common enclosure and pass the series type test. Its features are qualified as per GB/T17467-1998, DL/T537-2002, and IEC1330:1995. The substation is developed abiding to the specificity of wind-power generation as a new type of step-up device.
2 Service and Installation Conditions
Ambient temperature: -40℃~+40℃
Moisture: Daily average≤95%, Monthly average≤90%
Wind speed: Outdoor wind pressure≤700Pa (34m/s)
Seismic resistance Horizontal acceleration≤0.4m/s2, Vertical acceleration≤0.15 m/s2
Ambient temperature: The ambient environment should be without obvious pollution, such as corrosive or flammable gas or steem, and etc. The installation site should be without severe vibration.
Additional consultation between the user and manufacture should be needed, if the switchgear is to be operated in the conditions not in conformity with the above ones.